Waterman brand Chlorine Dioxide Generator is specially designed for water purification. It is a disinfection system of producing chlorine dioxide solution on site and adding them to water for disinfection, algae removal, bleaching, deodorization, etc.
It has many unique and prominent features of optimized structural design, good materials choice, good quality, low cost, safe and reliable operation and good applicability.
We always provide the most economical, reasonable and suitable disinfection solutions to our customers according to their special requirements and special circumstances of the scene.
CPF-D2 series ClO2 generator is a kind of positive pressure and automatic residual-chlorine-control disinfecting system. It is adopted Positive Pressure dosing technology for the first time in the world. It can brought disinfectant solution directly to the pressured water with simple, safe, reliable, stable operation and other characteristics. It can automatically adjust the dosage of clo2 solution through value of residual chlorine provided by the residual-chlorine-on-line control system.
The way of clo2 producing:
5NaClO2+4HCl = 4ClO2+5NaCl+2H2O
Use of raw materials:
Sodium Chlorite: 78% Industrial Sodium Chlorite
Hydrochloric Acid: 31% Industrial Hydrochloric Acid
Use sodium chlorite and hydrochloric acid as raw materials, transmission of raw materials through two metering pumps to the reactor, produce the concentration of more than 95% of high-purity chlorine dioxide solution added to water for disinfection. It can automatically adjust the dosage of clo2 solution through value of residual chlorine provided by the residual-chlorine-on-line control system. When lack of raw materials, the liquid level alarm system will give audible and visible alarm signals and automatically cut off the power supply of equipment. Raw materials conversion rate is more than 95%.
Working temperature: 5 ~ 40 degrees Celsius
Operating voltage: 220V plus or minus 10% / 380V plus or minus 10%
Operating current: <5A
There should be no strong electric field and magnetic field interference around equipment.
Maximum pressure of water-pipe-line: <0.7Mpa
Function: Residual-chlorine-on-line control, or manual control
Low liquid level alarm of raw materials
Linkage with water pump
| Index Model ||ClO2 Production (g/h) ||Disinfection capacity ||Overall Dimensions (mm) |
|Drinking Water ||Hospital Foul Water ||Swimming Pool Water ||Industrial Circulating Cooling Water |
|CPF-50D2 ||0~50 ||50~100 ||2.5~5 ||25~50 ||25~150 ||1400×470×1550 |
|CPF-200D2 ||0~200 ||200~400 ||10~20 ||100~200 ||100~600 ||1500×470×1620 |
|CPF-500D2 ||0~500 ||500~1000 ||25~50 ||250~500 ||250~1500 ||1800×550×1620 |
|CPF-1000D2 ||0~1000 ||1000~2000 ||50~100 ||500~1000 ||500~3000 ||2000×600×1860 |
|CPF-5000D2 ||0~5000 ||5000~10000 ||250~500 ||2500~5000 ||2500~15000 ||2400×660×1860 |